Hot taps added to three pipes
Client – DPC Mechanical Ltd
Location – Bromley-by-Bow, London E3
Task Appointed – To carry out 2x Hot Tapping’s Services on 80mm LTHW pipes
Hot Tapping Services Supplied – IDWe Ltd hot tapping team were asked to carry out 2 x hot taps on the existing 80mm flow and return heating pipework. The system could not be turned off or isolated so the only way to connect an additional service to this was to carry out hot tapping.
Services Completed Included – The hot tapping was done by welding on a 25mm pipe socket to the live pipework on both flow and return. We then fitted a 25mm quarter turn valve to both the flow and return. Next using a hot tapping rig, we drilled the live pipes and using the quarter turn valve to isolate the water before removing the hot tapping rig.
Result – There was no loss of water or disruptions to their heating services. The project was completed within one day, resulting in a very happy customer.
For further details on IDWe Ltd hot tapping services, please click here.
Get a quote, please call 020 8302 7644 or email email@example.com
To find out more about all of IDWe Ltd services, please click here.